How are Remote I/O and Distributed I/O Different?Let’s investigate the history of the terms Remote I/O and Distributed I/O and discuss what they mean today.
In this article, we’re going to talk about Remote I/O and Distributed I/O.
Depending on who you talk to, some say Remote I/O and Distributed I/O are the same thing and the terms are interchangeable … Not so says others.
So, who’s correct? Let’s investigate the history of the terms Remote I/O and Distributed I/O and discuss what they mean today.
Direct Digital Control or DDC system
Many vendors such as Taylor Instruments, Bailey Control, and Foxboro had DDC systems that centered on a mini-computer connected to several proprietary I/O devices located at remote locations around the plant.
Remote I/O vs Distributed I/O
Remote and Distributed in the context of locations
Today’s DCS is a control system that has a number of Distributed autonomous controllers each operating a number of continuous operations. The controllers are tied together via a centralized supervisory controller.
We’ve already used the terms Remote and Distributed in the context of locations of both I/O and controllers. It’s easy to see how the terms can be misunderstood.
Remote and Distributed I/O from PLC perspective
OK. Let’s have a look at Remote I/O and Distributed I/O from a PLC perspective. Remote I/O means that the I/O module is at a remote place physically located a distance from the control PLC.
Distributed I/O has a brain
As we mentioned earlier Remote I/O is sometimes also referred to as Distributed I/O. Let’s look at a definition for Distributed I/O that differentiates it from Remote I/O.
Generally speaking, Distributed I/O has a brain or some computing capacity. By default, it is Remote.
Allen-Bradley FLEX I/O
Allen-Bradley has FLEX I/O which is a modular I/O system for distributed applications. The Flex I/O allows for the connection of up to eight I/O modules and transfers I/O data to and from a central controller or PLC.
Flex I/O is an example of Distributed I/O and the eight modules connected to the Flex I/O are examples of Remote I/O.
Siemens ET 200SP
Siemens has the ET 200SP series of Distributed I/O that can connect up to 16 channels of digital or analog I/O with a single-wire connection.
The ET 200SP is an example of Distributed I/O and is connected to the bus system via an interface module. This system is very flexible as it can accommodate either PROFINET interface modules or PROFIBUS interface modules.
As we said earlier, Remote I/O is at a remote place physically located a distance from a control PLC. Remote I/O does not have a brain and is not capable of any computing function at all.
It’s likely safe to say that when you hear the term Remote I/O there is only one controller, or PLC, involved as opposed to Distributed I/O which has multiple controllers.
Let’s review what we’ve discussed.
– The predecessor of the DCS and the PLC was the Direct Digital Control or DDC system which centered on a mini-computer connected to several proprietary I/O devices located at remote locations around the plant.
– A modern DCS is a control system that has a number of Distributed autonomous controllers.
– Generally speaking, Distributed I/O has a brain or some computing capacity.
– Remote I/O does not have a brain and is not capable of any computing function at all.
– The term Remote I/O suggests a single controller such as a PLC, whereas the term Distributed I/O suggests multiple controllers.
Want to Learn More?
Newcomers to RealPars have free access to one of our online courses.
You can take advantage of this offer by downloading the RealPars app (iOS, Apple TV, Android, Android TV, FireTV, Roku) and selecting the first lesson of the PLC Hardware course. Just like the video, the lessons are all high-quality and also very easy-to-follow.
Also, for a low monthly fee, you’ll get full access to an exclusive library of courses on PLC programming and industrial automation topics as well as new fresh out of the oven videos each and every week. These courses are all member-exclusive and are not shared anywhere else on the internet.
If you would like to get additional training on a similar subject please let us know in the comment section.
Check back with us soon for more automation control topics.
Got a friend, client, or colleague who could use some of this information? Please share this article.
In this blog post, you’ll learn about the mindset that helped me getting a PLC programming job with NO experience. This is my personal experience as someone who searched for a job in this field and as an employer who reviews resumes and interviews candidates for a variety of projects. So let’s get started!
In this article, we’re going to discuss a very common flow measuring device called a Turbine Flow Meter.Depending on who you talk to, a Turbine Meter has one or two major parts. Some will tell you that the Turbine Meter has only one part: the Mechanical component....
In this article, we're going to talk about Sinking and Sourcing PLC digital output modules and how they connect to field devices.As we’ve discussed in our other articles, the two types of PLC output modules are Digital and Analog. Drilling down even further, Digital...
Learn how to program PLCs, install and wire industrial devices, and at the same time purchase them online.
+31 10 316 6400
Mon - Fri 8:30 am to 5:30 pm (CET)
Rotterdam Science Tower, Marconistraat 16,
3029AK Rotterdam, Netherlands
© 2021 RealPars B.V. All rights reserved.
Created with coffee and tea in Rotterdam.