What is High-Performance HMI?Let’s move away from poorly designed HMIs and learn about the High-Performance HMI.
High-Performance HMI is the industry answer for a standardized, easy to use, and more productive HMI graphics system to implement and in some cases, replace a poorly designed HMI.
As we know, operator control of processes is done using a graphical representation of the process, known as an HMI, or Human Machine Interface.
A properly designed HMI
A properly designed HMI will support a smooth and stable operation of the process as well as notify the operator of an abnormal condition. However, this isn’t always the case.
Many HMIs were poorly designed and implemented, leading to situations that can compromise safety, quality, and profitability.
Many current HMIs make use of
– a broad spectrum of colors,
– unnecessary graphics,
– visual distractions, and
– lack of overall situational awareness.
These, in turn, can result in negative consequences.
Some of these consequences can include poor operating procedures, such as running by the alarms, where an operator is only responding to alarms and not understanding the root cause of the alarm conditions.
In other cases, a poorly designed HMI will result in avoidable upsets and increase the likelihood of less than the optimum response to an abnormal situation.
In the worst cases, a poorly designed HMI has been identified as a contributing factor in some industrial accidents.
You can an example of a poorly designed HMI below.
HMI design requirements
Let’s talk about how we got here. Early HMIs were simple depictions of the P&ID of the process that they were controlling and monitoring. This was mostly from the limitations of the computing and graphics power of the times.
As computing power and graphics processors advanced, so did the mindset that a highly complex, data-filled, and visually striking HMI should follow.
We see flickering flames to represent a flare, moving rail cars in loading bays, some have gone as far as to take digital photos of the actual process floor and overlay data on the HMI screens!
Add this mindset to the thousands of systems integrators, and we end up with an industry with no standard displays. Even identical processes can have vastly different HMI screens, depending on who implemented them and customer desires.
There are HMIs all around the world with
– inconsistent navigation,
– difficult to understand data being presented,
– improper alarm depictions, and
– a lack of display methodologies
presenting the state of the operating equipment.
ISA-101 HMI design standard
Let’s move away from these HMIs and learn about the High-Performance HMI.
In 2003, the International Society of Automation, or ISA, tasked a group of end-users, operators, and engineers to start working on a standard.
In 2015, twelve years later, they published the ISA-101 HMI Design Standard. It is the set of guidelines, principles, and philosophies for developing graphics on a process HMI. This standard is meant to create
– a more functional,
– easy to understand, and
Proper use of color
Here we are going to cover the basic concepts of High-Performance HMI. One concept is the proper use of color. Moving away from the intense and colorful graphics, the High-Performance HMI is developed in grayscale, with color intended to be the attention-getter.
Gone are the days of red and green to indicate running or not running. In a grayscale screen, the use of color is meant to indicate an abnormal situation very quickly. It has been shown that the new use of color alone has resulted in a 48% improvement in detecting abnormal situations before alarms occur.
A grayscale screen with no color present means a normal operating plant with no alarms. A quick glance by an operator can confirm this and productivity can increase as the operators do not have to spend time studying a screen to look for abnormal situations.
Use of information over data
Another concept is the use of information over data. Many HMIs will have dozens or more data points visible on the screen, but nothing for an operator to determine what that data means.
A pressure indicator could read 900 psi, but is that a good thing or a bad thing? By utilizing an indicator of normal range with a process variable, the operator can make a quick decision to take action to correct a situation that is trending away from normal.
High-performance HMI trends
Speaking of trends, we now are seeing embedded or always visible trends on important process variables. By making these trends always visible, the operator can see a quick overview of historical data and evaluate for any necessary process adjustments before a product runs out of specification or a tank overflows, both time consuming and costly mistakes that can now be avoided.
Keeping the screen simple
A very important concept in High-Performance HMI is keeping the screen simple and uncluttered. A simple depiction of a vessel with a valve and pump is all that is necessary. Along with that are easy to find navigation buttons that will take the operator to the next step in the overall process.
High-performance HMI colors
There is no need to show bulkhead fittings, flanges, or non-essential 3D pipe objects. Instead, an ISA valve and pump, using a line to depict process flow are the standard.
When depicting the status of a pump or valve, instead of red and green for running or not running on a pump or open and closed on a valve, High-Performance HMI will use a dark gray status for a pump that is stopped and white for a pump that is running. For a pump that does not send feedback to SCADA, it will be depicted as medium gray.
High-performance HMI display hierarchy
Proper display hierarchy is critical to a High-Performance HMI. By creating a hierarchical system of displays, the operators can have overall situational awareness, and the ability to drill down to very specific data points when necessary.
There are four levels of hierarchy in the High-Performance HMI.
1) Overall situational awareness
Level 1 is used for overall situational awareness. An operator can see the entire process at a very high level from this screen.
2) More detailed view
Level 2 is a screen that an operator can access to view a smaller and more detailed view than Level 1. Level 2 will call a sub-system or process in greater detail than Level 1.
3) Equipment details
Level 3 is the equipment details screen, such as a pump or a valve. It will include even more detailed data on that particular process.
Finally, Level 4 is the diagnostics screen. This will give the operator access to very detailed information on a processing device and is accessed for troubleshooting purposes.
High-Performance HMI is still a moving target and is still subject to the preferences of the stakeholders. However, it has been shown that when presented with the concepts of High-Performance HMI, operators are eager and excited to implement it into their system.
While all systems are different, utilizing a more standardized model will vastly improve productivity, quality, and safety. Thank you for watching this video, and be sure to look for Part 2, High-Performance HMI Design Basics.
Some of the graphics and the HMI screens used in this video are from the High-Performance HMI handbook which is a great reference if you want to dig deeper into this topic.
If you have any questions about High-Performance HMI and Design standards, add them in the comments below and we will get back to you in less than 24 hours.
Got a friend, client, or colleague who could use some of this information? Please share this article.
By Gregory Duranso
Posted on Dec 7th, 2020
By Gregory Duranso
Posted on Dec 7th, 2020
In this blog post, you’ll learn about the mindset that helped me getting a PLC programming job with NO experience. This is my personal experience as someone who searched for a job in this field and as an employer who reviews resumes and interviews candidates for a variety of projects. So let’s get started!
There are dozens of manufacturers of Programmable Logic Controllers that are used in the automation industry. One of the leading makers of compact PLCs for machine automation is Omron PLC. Omron offers a flexible line of scalable industrial PLC controllers for use in...
In this article, we're going to explore the differences between Solid State and Relay outputs on PLC Digital Output Modules. We’re also going to talk about the pros and cons of each.The purpose of a PLC Output module is to operate or control a physical device based on...
Learn how to program PLCs, install and wire industrial devices, and at the same time purchase them online.
+31 10 316 6400
Mon - Fri 8:30 am to 5:30 pm (CET)
Rotterdam Science Tower, Marconistraat 16,
3029AK Rotterdam, Netherlands
© 2021 RealPars B.V. All rights reserved.
Created with coffee and tea in Rotterdam.